If you want to see a good picture of a large circuit breaker that has been damaged by an arc blast, look at the pictures with this blog. The breaker was a Westinghouse PC32000 molded case circuit breaker. It was a 2000 amp circuit breaker that failed to interrupt a fault and blasted the inside of the breaker until it actually blew a hole through the side of the circuit breaker frame. If you look closely, you will see where a MIDWESTswitchgear service technician actually stuck a screwdriver through the hole. The close up picture shows the hole and shows the extensive arcing damage to the moveable arcing and main contacts. The phase barriers, arc chutes, pretty much the whole Westinghouse PC32000 circuit breaker, was arc blasted beyond repair. One picture shows the destroyed circuit breaker next to a MIDWEST inventory stock PC32000 circuit breaker. This is a tough Westinghouse molded case circuit breaker. It wouldn’t make any difference whether the breaker was Square D or GE General Electric. If the breaker contacts begin to open, but fail to interrupt the current, arc damage will quickly occur. If the breaker is trying to interrupt fault current, extensive arc damage occurs very fast and will quickly expand into a phase to phase fault with catastrophic destruction. The arcing fault may explode outside the case of the circuit breaker. This is one of the reasons for wearing protective clothing and following safe work practices when operation circuit breakers. Bad things can happen very fast. Too fast for you to get out of the way. We suggest being paranoid about safety when working around electrical power equipment.
Archive for December, 2011
December 29th, 2011 9 comments
Categories: Uncategorized 2000 amp circuit breaker, arc blast, arc chutes, arc damage, arcing damage, Damaged Circuit Breaker, Electrical Power Equipment, Extensive Arcing Damage, GE Circuit Breaker, General Electric Circuit Breakers, PC32000 Circuit Breaker, Phase Barriers, Phase to Phase Fault, Protective Clothing, square d circuit breaker, Westinghouse Circuit Breaker, Westinghouse PC32000 Circuit Breaker