Circuit Breaker Reset Tests
A customer called MIDWEST to ask why we did something called a “Reset Test” on his circuit breaker. He said he has had circuit breakers tested by switchgear service companies for nearly 30 years and never ever saw something called a circuit breaker “Reset Test.” He has Square D circuit breakers, Westinghouse circuit breakers, General Electrical circuit breakers and newer Cutler Hammer circuit breakers. He checked some of his old test reports and found no “reset tests.” He had never used MIDWEST before, so he was pretty interested when we explained the reason and procedure for the reset test. The reason was a very pleasant surprise because it gave him greater confidence in the proper performance of his circuit breakers. MIDWEST started using the circuit breaker “reset test” many years ago. It’s not a standard test procedure. You won’t find it in the text books or instruction manuals. You will find it in MIDWEST’s Training Manual under ‘Scars,’ meaning experience. It’s a carry over procedure from testing old dashpot type air circuit breakers and insulated case circuit breakers and molded case circuit breakers. The reason for the test is that occasionally, seldom but occasionally, a circuit breaker will nuisance trip when put back into service after it has been high current tested. For example, a 1600 amp air circuit breaker, after high current testing, might nuisance trip instantly at 500 amps. Basically the over current device failed during the high current testing. This was far more common with older “non electronic” over current devices. New electronic over current devices are more reliable, but not perfect. Strange things happen. We are not talking about the service technician forgetting to put the settings back to the correct positions. We are talking about an actual defective device. The test only takes moments. In the interest of quality control, the reset test addresses the “consequences of failure” as opposed to the “probability of failure.”
Yes, we are paranoid about safety and quality.